LV Cable Commissioning
From Open Electrical
Revision as of 06:51, 15 February 2017 by Jules (Created page with "== Visual Inspection == :* Check cable mechanical connections :* Check that cable colour codes conform to project specifications and/or national standards :* Verify cable tags...")
- Check cable mechanical connections
- Check that cable colour codes conform to project specifications and/or national standards
- Verify cable tags / numbers
- For each test, record the testing instrument make / model and serial number.
- Perform insulation-resistance test (megger) on each conductor with respect to earth and adjacent conductors. For 0.6/1kV cables, an applied voltage of 1,000 Vdc for 1 minute is appropriate, with acceptance levels of 100 M[math]\Omega[/math] for new cables and 1 M[math]\Omega[/math] for aged cables.
- Perform continuity (point-to-point) tests to ensure proper cable connection and continuity. Where applicable, perform continuity tests on each phase to neutral and each phase to phase and record the readings in Ohms.