# LV Cable Commissioning

• Perform insulation-resistance test (megger) on each conductor with respect to earth and adjacent conductors. For 0.6/1kV cables, an applied voltage of 1,000 Vdc for 1 minute is appropriate, with acceptance levels of 100 M$\Omega$ for new cables and 1 M$\Omega$ for aged cables.